A 398 KW MV motor that runs a blower fan in a cement plant was showing strange behavior. The vibration equipment indicated vibration amplitudes that became chronic with the passage of time. The maintenance team, not knowing what the issue was, ran the motor until the bearings had to be replaced...
- Mark Koch
- ALL-TEST Pro, LLC